The EL-LEG Recessed Emergency Light is constructed from 20-gauge steel back box with junction box, trim plate is constructed out of aluminum. Friendly configuration design for quick and easy installation.
The EL-LEG Recessed Emergency Light use long-lasting, efficient ultra bright white LEDs CCT 5000k. Equipped with 2 adjustable LED lamps.
Upon failure of the normal utility power, an internal solid-state transfer switch automatically provides uninterrupted emergency operation for at least 90 minutes. The fully automatic solid-state, two-rate charger initiates battery charging to recharge a discharged battery in 24 hours.
BATTERY - BATTERY BACKUP
The EL-LEG Recessed Emergency Light is designed with a maintenance-free 3.6V 1800mAh LiFePO4 battery that provides a minimum emergency duration of 90 minutes. Recharge time of the battery is 24 hours.
|50°F to 104°F
Total Luminaire Lumens : 400lm
Input Wattage: 2.0
Input mA: 22
Standard mounting height of 7.5ft illuminates 1 footcandle (FC) spaced at 42ft for a 3ft path of egress.
Standard mounting height of 10ft illuminates 1 footcandle (FC) spaced at 48ft for a 3ft path of egress.
Spacing is measured in lab condition with an assumed open space, no obstruction and reflection rates of 80 (ceiling) / 50 (walls) / 20 (floor). Actual spacing may vary depending on what environment the fixture is installed in.
Continuously monitors the AC power, battery supply voltage, emergency lamp and charging circuit. The multi-color LED indicator light will indicate failure and adjust when it has been corrected. Unit will automatically perform NFPA required monthly and annual testing. Self-testing will take place once a month for 3 minutes and 90 minutes once a year.
Universal voltage input 120/277 VAC 50/60Hz operation. LED display indicates AC/ON. An external push button test switch allows maintenance personnel to quickly determine the operational status of the unit. Features battery over discharge protection.
The EL-LEG is suitable with drywall or drop ceiling mount installations.